Profine® filter cartridge
The new Profine Pfas cartridge has been created to give a concrete solution to Pfas problems. With the Profine Pfas system you can turn back to drinking your tap water. Cartridge performance is not affected by other unwanted substances; Pfas once detained are no longer released in any way, thus guaranteeing the highest quality of service. With the Pfas Kit, made up of two cartridges, the clogged, unpleasant flavors and smells of drinking water are also removed. The device operates at mains pressure without the help of pumps.
PROFINE® PFAS removes Perfluorocarbons PFCs and bad odours and off-tastes in drinking water. It is a disposable cartridge with Perfluorocarbons PFCs selective resin for the treatment of drinking water. The PROFINE® filter with bayonet mount is built with the strong anionic resin and has a stage of final filtration with 0.5 micron nominal and Profine® Carbon Block with silver. Used at point of use, for drinking water with PFC concentration.
|Function flow rate||2 l/min*||2 l/min*|
|Working pressure||Min. 2 – Max. 6 Bar||Min. 2 – Max. 6 Bar|
|Temperature||Min. 4 Max. 30°C
|Min. 4 Max. 30°C
|Capacity||11.000 l*||11.000 l*|
- Flow rates can vary, even to a considerable extent, depending on the quality of the incoming water.
Medium cartridge mustn’t be used singularly.
WARNING: use in accordance with the directions.
External diameter: 87.4 mm
Medium cartridge high: 384 mm
Large cartridge high: 529 mm
DISPOSE OF THE SPENT CARTRIDGE RESPONSIBILY
Dispose the exhausted cartridge in compliance with Decision 2000/532/CE (code 15 02 03 EWC).
TABLE OF CHEMICAL AND CHEMICAL-PHYSICAL WATER ANALYSIS
References to chemical analysis and chemical-physical proprieties of water as a reference by the manufacturer are inserted, both for the definition of the conditions of use and of the maintenance, and the period of use the equipment.
CHECK OF PARAMETER CHANGE
|ParametER||REGULATORY REFERENCE (D.LGS 2 FEBRUARY 2001, N ° 31 AND SUBSEQUENT RECIPIENTS PART C PARAMETERS INDICATORS)||UNTREated water||TREATED WATER||Note|
|PFAS PFOS||—||250 ng/l||0,0 ng/l|
|Aluminium||0,20 mg/L||≥ 0,006 e ≤ 0,012 mg/L||≥ 0,004 e ≤ 0,002 mg/L|
|Amonium (NH4)||0,50 mg/L||0,00 mg/L||0,00 mg/L|
|pH (Hydrogen ion concentration)||≥ 6,5 e ≤ 9,5||≥ 8,2 e ≤ 8,3||≥ 8,1 e ≤ 8,4|
|Iron||0,20 mg/L||≥ 0,15 e ≤ 0,17 mg/L||≥ 0,003 e ≤ 0,005 mg/L|
|Pseudomonas Aeruginosa||0 UFC/250 mL||0 UFC/250 mL||0 UFC/250 mL||Check afeter 30 days of no use|
|Solphate |||≤ 250 mg/L||≥ 29,1 e ≤ 30,5 mg/L||≥ 23,9 e ≤ 28,1 mg/L|
|Bacteria growth at 22°C and at 37°C||0 UFC/250 mL||—||No abnormal change||Check afeter 30 days of no use|
|Coliform Bacteria at 37°C||0 UFC/250 mL||0 UFC/100 mL||0 UFC/100 mL||Check afeter 30 days of no use|
|Active chlorine (Residual disinfectant)||0,20 mg/L||≥ 0,09 e ≤ 0,12 mg/L||≥ 0,02 e ≤ 0,04 mg/L||-85%|